Water purification station
- Reagent-free purification of artesian water for household and drinking consumption. (deferrization, removal of iron, odor, color, turbidity and other contaminants).
- Reagent purification of river surface water for household and drinking consumption (removal of iron, color, turbidity and other contaminants.
Artesian water purification technology:
Pump in the well → Air degassing → Contact filtration → Pump for consumption
River surface water treatment technology:
Water intake → Reagent dosing and Contact filtration → Pump for consumption
To change the quality of water treatment; there is a technological recycle of water for the purpose of additional purification and / or additional purification of water, up to the required parameters, as well as for heating the “ice” water by several degrees.
Location of the containerized installation:
On the bypass of the customer\’s existing discharge pipeline.
Initial water pressure at the unit inlet: not less than 0.10 atm.
Purified water pressure for consumption (at design capacity): 4.0 atm.
The flushing water is discharged from the installation at a pressure of 1.0 atm. Therefore, the installation can be located below ground level.
Installation flushing frequency: from 1 time per week to 1 time per month (at a concentration of all removed contaminants: from 40 to 5 mg / l).
Flushing water volume: up to 10 m3 in 10 minutes.
Purified water tank: 11 m3
Automatic control over the operation of the pump in the well (on / off) from the pressure sensor.
When the consumption of water for consumption changes, the consumption of electricity for water purification changes proportionally.
The main materials for the manufacture of the installation: plastic and polymers.
Thermal insulation, for use in adverse climatic conditions, including:
for the regions of the Far North
for African countries
Natural or forced ventilation of the container.
Air conditioning in the container: from the cold surface of the installation with running water.
Heating: Electric or water (from the customer\’s heat carrier)
Foundation: reinforced concrete slabs, or pile-frame base
Total specific power consumption for artesian water purification and supplying it for consumption (4 atm.): 0.58 kW / m3.
Transformer: 50 kW (380 volts), for Deferum-1500
Instrumentation and automation: Automatic control of the water treatment plant is based on replaceable logic modules with software control.
The customer is given an instruction and a laptop with a mnemonic diagram to control and / or change the parameters of the installation, if necessary: via a mobile phone.
Total specific power consumption for surface water purification and supplying it for consumption (4.0 atm): 0.25 kW / m3.
Transformer: 25 kW (380 volts) for Deferum-1500
Disinfection of purified water, if necessary: separate delivery
Unit Deferum-500 m3 / day of container type, located in a 20-foot container.
For test tests, we offer a light and mobile unit Deferum-05 m3 / h.
We are near
st. Yasnaya 3, Rivne, Ukraine, 33001